Bahra Cables Company was established in to serve Saudi & GCC Markets. . This Catalogue is intended for Medium Voltage Power Cables, Aluminum. MEDIUM VOLTAGE POWER CABLES CONTENTS GENERAL 1 INTRODUCTION TECHNICAL 4 INFORMATION Single Core XLPE Insulated. TECHNICAL INFORMATION COPPER CONDUCTOR | STEEL TAPE ARMOURED | /15 ()kV Size mm2 25 35 50 70 95
|Published (Last):||25 August 2015|
|PDF File Size:||7.31 Mb|
|ePub File Size:||2.71 Mb|
|Price:||Free* [*Free Regsitration Required]|
The protective cable end cap should not beremoved from the ends of the cable until immediately prior to termination or jointing, especiallyfor cables that do not have extruded bedding. This isimportant in wet or other aggressive environments.
If the cable is not suitable for wet applications and the underground water engrossed inside it,replacing the defected section from joint to joint is the recommend solution. Medium Voltage updated LowRes. The cagalogue given in the tables are for one circuit installed thermally isolated from other circuits or any other heat source. The armour provides mechanical protection against crushing forces.
Bahra Cables Medium Voltage Catalogue
The organization has a lean vertical management structure which is designed to integrate witha highly developed IT-based structure. For cables specified in this standard, a longer period, not exceeding 8 h on any occasion, can be tolerated. A non-hygroscopic polypropylene filler is applied between cata,ogue up cores to providea circular shape to the cable. Bahra Cables Company is committed to the production of the best product quality and service,utilizing cutting edge European Technology cataloghe its manufacturing.
Cable special features required, e. Roll in the direction shown by the arrow. The volume resistivity of thisexternal layer is limited to meter-ohms.
A 2- Laid in free air both end bonded Trefoil Bhara Approx. This layer, which has a very smooth surface, is a transition form the insulatingmaterial where the electric field exists to a conductive metallic screen, where the electricfield is zero, so it will reduce the stress enhancement at the insulation layer.
Lift drums on fork trucks correctly.
Bahra Cables Company
Product Reliability is starting from the time of product design to fit for the intended application and environmental conditions, to the selection of the raw material from only the highest class suppliers with internationally trusted reputation. Manufacturing malfunction, which Bahra Cables Company guarantees its product againstany defect or wrong workmanship, meanwhile in case of damage due to this reason, the actionwill be taken as per the submitted warranty letter, and the company will apply the requiredcorrective and preventive actions.
During the test, the voltage should be increased gradually to the full value and maintainedcontinuously for 15 min. Fire or excessive temperature at the cables cataogue.
Conductor required cross sectional area. The nominal system voltage U, up to 1. Insulated conductor diameter mmd: Load current A R: The PVC or PE jacketing material is very stable against most of the Chemical traces could be existing at the soil, these material with Black colour Master batch up to 2. The built-up area, including offices and plant, of start up phase is more than 62,sqm.
The basis of the standard conditions is the climate conditions of the Kingdom of Saudi Arabia, which are: Voltage between phases conductors 2. Flat Touching Formation Approx. Axial spacing between cables Trefoil formation S: The total duration of earth faults in any year should not exceed h. When testing is required after cables have been in catalotue of service duration, Bahra Cables Cstalogue Technology Department should beconsulted for the appropriate test conditions, which depend on the individual circumstances.
The shape codes are rmc, round compacted stranded 2. It excludes transient voltage variations, due, for example, to lightning impulses, fault conditions and rapid connection of loads. Short circuit for t second kAIsc 1: As Insulation treeing caatalogue uncommon problem for LV cables, the chance of electric break down is very minor.
Bahra Cables Medium Voltage Catalogue
No breakdown should occur. Read the Text Version. We are working in different axes canles completely fulfill customers satisfaction which is the milestone of cabless business, such axes are: Such cooperation in knowhow is invested to provide our customer with the best service and support.
A A 2- Laid in free air both end bonded Trefoil Formation Approx. Cables are often supplied in heavy cable reels and handling these reels can constitutea safety hazard. Product quality complying with the local and international standards 2.
Read the Text Version. It specializes in Manufacturing and Distributing Electric Cables. The test voltages given above are intended for cables immediately after installation and not forcables that have been in service. This period, according to IECshould not exceed 1 h.
Please contact the Technology Department for any query. Bahra Cables Factory occupies over ,square meters of prime manufacturing space together with associated design offices, laboratoriesand storage area. Single-core cables are suitable for d.